.5 Setpoint Lock
A switch on the back of the front module can be used to lock the setpoint.
The configuration parameters appear in the order shown below.
Remove the front module from the
back plate to access the switch.
°C or °F
Heating cycles per hour 1
Place the switch (S1) to the I posi-
2, 3, 4, 5 or 6 2
Cooling cycles per hour 1
2, 3, 4, 5 or 6 2
Reinstall the front module.
2H (2H1C) or 1H (1H1C)
HP (Heat Pump) or Cn (HVAC)
H1C type 3
When either the heating or the cooling parameter is displayed, use the
mode selector switch to toggle between the two parameters.
Power supply: 24 VAC
Maximum load: 1.5 A per output @ 24 VAC
Setpoint range (heat): 5 to 28°C (41 to 82°F)
Setpoint range (cool): 15 to 35°C (59 to 95°F)
Setpoint increment: ± 0.5°C (1°F)
Display range: -5 to 50°C (23 to 122°F)
Display resolution: 0.5°C (1°F)
The corresponding cycle lengths are: 2 = 30 min., 3 = 20 min.,
= 15 min., 5 = 12 min., 6 = 10 min.
This parameter appears only if you select 1H1C for the system type.
To access the configuration menu, press and hold both temperature
adjustment buttons for more than 3 seconds.
To go to the next parameter, once in the menu, press both temperature
adjustment buttons for more than 2 seconds.
Short-cycle protection: 2 minutes
Storage temperature: -20 to 50°C (-2 to 122°F)
Dimensions: 79 mm x 81 mm x 25 mm (3.1 in. x 3.2 in. x 1.0 in.)
To modify the displayed parameter, press one of the temperature adjust-
You will exit the configuration menu at the end of the menu.
Aube warrants this product, excluding battery, to be free from defects in the
workmanship or materials, under normal use and service, for a period of three (3)
years from the date of purchase by the consumer. If at any time during the warranty
period the product is determined to be defective or malfunctions, Aube shall repair
or replace it (at Aube's option).
If the product is defective,
i) return it, with a bill of sale or other dated proof of purchase, to the place from
which you purchased it, or
Note: The settings are not erased during a power outage.
4.1 System Mode
Use the system mode selector switch to place the system in heat
mode, cool mode, emergency heat (E.H.) mode, or off.
ii) contact Aube. Aube will make the determination whether the product should be
returned, or whether a replacement product can be sent to you.
This warranty does not cover removal or reinstallation costs. This warranty shall
not apply if it is shown by Aube that the defect or malfunction was caused by
damage which occurred while the product was in the possession of a consumer.
Aube's sole responsibility shall be to repair or replace the product within the terms
stated above. AUBE SHALL NOT BE LIABLE FOR ANY LOSS OR DAMAGE OF
ANY KIND, INCLUDING ANY INCIDENTAL OR CONSEQUENTIAL DAMAGES
RESULTING, DIRECTLY OR INDIRECTLY, FROM ANY BREACH OF ANY
WARRANTY, EXPRESS OR IMPLIED, OR ANY OTHER FAILURE OF THIS
PRODUCT. Some provinces and states do not allow the exclusion or limitation of
incidental or consequential damages, so this limitation may not apply to you.
THIS WARRANTY IS THE ONLY EXPRESS WARRANTY AUBE MAKES ON THIS
PRODUCT. THE DURATION OF ANY IMPLIED WARRANTIES, INCLUDING THE
WARRANTIES OF MERCHANTABILITY AND FITNESS FOR A PARTICULAR
PURPOSE, IS HEREBY LIMITED TO THE THREE-YEAR DURATION OF THIS
WARRANTY. Some provinces and states do not allow limitations on how long an
implied warranty lasts, so the above limitation may not apply to you.
Note: Emergency heat mode is not available on 1H1C systems.
For these systems, placing the selector on E.H. is the same as
placing it on Off.
Only 2H1C systems are equipped with auxiliary heat. The auxiliary heat is
used in the following conditions:
When the setpoint is not attained after a 15-minute delay following the
compressor activation. After the delay, the auxiliary heating is used along
with the compressor.
When the thermostat is placed in emergency heating (E.H.). In this mode,
only the auxiliary heat is used.
.2 Fan Mode
Use the fan mode selector switch to place the fan in automatic
mode (AUTO) or continuous mode (ON).
This warranty gives you specific legal rights, and you may have other rights which
vary by province, state or region.
Note: This switch is not functional if the fan is not connected to
For any questions regarding product installation or operation, contact our
The fan operates only when heating or cooling is activated.
The fan operates continuously.
technical support team at:
.3 Viewing and Setting the Temperature
The actual temperature is normally displayed. To view the setpoint, press
once on one of the temperature adjustment buttons. The setpoint is displayed
Tel.: (450) 358-4600
Fax: (450) 358-4650
for 5 seconds and is indicated by the
icon display. To change the setpoint,
press the appropriate temperature adjustment button during the setpoint dis-
For more information on our products, visit us at
The display illuminates for 12 seconds when either of the temperature adjust-
ment buttons is pressed.