Model Selection (switch)
Temperature Lock (TH1 1 3 only)
TH1 1 3 & TH1 1 6 A/ꢀ/Aꢀ
FOR A AND AF MODELS ONLY
At the rear of the control module is a switch that has been
factory-set to the applicable temperature control.
At the rear of the control module are two potentiometers.
These potentiometers act like a temperature lock. Even
when occupants adjust the temperature using the dial on
the front/rear of the control module, the potentiometers
override the dial and maintain the temperature within the
locked-in minimum and maximum range.
A - ambient temperature
F & AF - floor temperature limit
Use a flat tip screwdriver to rotate the potentiometers until
the notch points to the desired temperature.
Turn the dial to the desired temperature.
TH113: The dial is located on the front of the control
TH116: The dial is located on the rear of the control
Thank you for choosing Aube’s non-
programmable thermostat. Your new
electronic thermostat is equipped with a
microprocessor and proportional integral
NOTE: The AF model can be used for all temperature
control types (A, F and AF).
The min. position indicates the minimum temperature
setpoint: 45°F (7°C).
Note: The ambient
sensor is not
operational when the
switch is set to I (up).
technology for total comfort. Depending on
the selected model, this thermostat has been
designed to control:
A: The Ambient temperature (using an
electric heating system)
AF: The Ambient temperature with Floor
temperature limit (using a floor heating
system to heat the room)
F: The Floor temperature (floor heating)
NOTE: This control module must be
mounted on a PB112 Series power base.
The thermostat has an On/Standby switch
making it possible to put the thermostat in
sleep mode when its use is no longer
required (e.g. summer).
Control Module Installation
AUBE TECHNOLOGIES INC. ONE (1) YEAR LIMITED WARRANTY
Align the bracket tabs on the control module with the
holes located on the power base.
The GFCI monitors the electrical
flow for any loss of current; if
there is any loss, the thermostat
will cut off power to the heating
system. We recommend you test
the GFCI immediately after
installing the control module, and
This product is guaranteed against workmanship defects for a one year
period following the initial date of purchase. During this period, AUBE
Technologies Inc. will repair or replace, at our option and without charge,
any defective product which has been used under normal conditions. The
warranty does not cover delivery costs and does not apply to products
poorly installed or randomly damaged following installation. This warranty
cancels and replaces any other manufacturer's express or implied
warranty as well as any other company commitment. AUBE Technologies
Inc. cannot be held liable for related or random damages following the
installation of this product. The defective product as well as the purchase
invoice must be returned to the place of purchase or mailed, prepaid and
insured, to the following address:
The TH113 and TH116 are equipped with a remote input
which allows connection of an optional telephone
controller (CT240) or any other remote control system.
When a command signal is received through this input,
the thermostat automatically lowers its setpoint by 3.5°C.
The LED lights up to indicate the signal’s presence
Follow the same procedure for the TH116.
except for GA and GB models).
month thereafter to
Bypass (not available for GA and GB power base):
The TEST button can be used to bypass the signal for a
ensure it is operating properly. To
Aube Technologies Inc.
-hour period. The LED goes off to indicate the bypass.
Press the TEST button:
NOTE: When combined with a GA/GB power base, the
TEST button is used only for GFCI testing. The bypass
function is not available with these power base models.
Saint-Jean-sur-Richelieu, Quebec, Canada J2X 5K8
Successful: TEST warn-
ing light is ON and power to heating system is cut
If you have any questions concerning the TH113 or the TH116
thermostat, call our technical support team at:
Unsucessful: The TEST warning light is OFF. Cut
power to heating system from the main power
panel and call customer service.
Models: TH113 and TH116 A / AF / F
Phone: Montreal area: (450) 358-4600
Canada / U.S.: 1-800-831-AUBE (2823)
Setting range: 45°F, 59°F to 95°F (7°C, 15°C to 35°C)
Potentiometers: minimum: 41°F to 77°F (5°C to 25°C)
maximum: 59°F to 95°F (15°C to 35°C)
Accuracy: ± 0.9°F (0.5°C)
When successful, reset thermostat (STANDBY/ON)
to power heating system.
NOTE: Keep the thermostat's air vents clean and free
NOTE: If the test warning light comes ON during normal
operation, cut power to heating system from the main
power panel and have an electrician verify the installation.
Monday to Friday from 8:30 AM to 5:00 PM EST.
For more information on our products, visit us at:
Storage: -4°F to 120°F (-20°C to 50°C)
NOTE: The screw cannot be removed completely.