HOLE OR KNOCKOUT FOR
CAD CELL LEADS
The TRADELINE intermittent ignition oil primary control
operates the oil burner, oil valve (if desired) and the ignition
transformer in response to a call for heat from the thermo-
stat. Through a C554 Cad Cell Flame Sensor, the R8184
monitors the burner flame and shuts down the system on
emitting diode (LED) on the terminal strip lights when the
safety switch opens to provide safety shutdown indication.
A manual reset button is provided to reset the safety switch
x 4 JUNCTION
For convenience in system maintenance, the safety
switch can be manually opened using a lever on the front of
the control. Clock thermostats that power the clock through
the primary control transformer will lose time during lockout
unless backup batteries are installed.
ratories Inc. and meets their flammability test requirements
for a final enclosure.
STRIP WIRES 3/8 in. (9.5 mm); INSERT FROM SIDE, ABOVE OR BELOW.
T-T TERMINALS ON R8184G; T1-T2 TERMINALS ON R8184N.
Fig. 1—Mounting the R8184G controls with 130° F
54° C] maximum ambient temprature.
WHEN INSTALLING THIS PRODUCT…
1. Read these instructions carefully. Failure to follow
them could damage the product or cause a hazardous
1. Mount on a 4 x 4 inch junction box, directly on the main
burner, or inside the appliance cabinet. In replacement
applications, mount in the same location as the old control.
2. Ensure the operating temperatures are within the am-
bient temperature range. Ambient temperature ranges are
either -40° to 130° F [-40° C to 54° C] or -40° F to 150° F
[-40° C to 66° C] (Refer to box label).
2. Check the ratings given in the instructions and on the
product to make sure the product is suitable for your
3. Installer must be a trained, experienced service tech-
4. After installation is complete, check out product op-
Wiring must comply with all local codes and ordinances.
Before mounting the control, make line voltage connec-
tions as shown in Fig. 1 or 2. Splice leads with solderless
connectors. Do not exceed load ratings shown on the device
If cad cell leads are run with line voltage wires, breakout
knockout at the bottom of the low voltage terminal strip and
thread can cell leads through the hole.
eration as provided in these instructions.
. Disconnect power before beginning installation to
prevent electrical shock or equipment damage.
. Make sure combustion chamber is free of oil or
vapor before starting system.
If necessary use control as a template to mark and drill new
mounting holes. Mount using No. 6 screws (obtain locally).
R8184G PROTECTORELAY CONTROL
POWER SUPPLY. PROVIDE DISCONNECT MEANS AND OVERLOAD PROTECTION AS REQUIRED.
TO USE R8184 WITH LINE VOLTAGE CONTROLLER, JUMPER T-T TERMINALS AND CONNECT LINE VOLTAGE THERMOSTAT IN
SERIES WITH LIMIT CONTROLLER.
Fig. 2—Typical hookup for TRADELINE R8184G with indicator light.
Form Number 69-0617—1
© Honeywell Inc. 1991